+1 310.318.7151

Mon - Fri: 9:00AM - 6:00PM

info@esgrounding.com

# What Is An Acceptable Earth Ground Resistance Value?

Our Response:
The NEC states that if you use one ground rod that the resistance to ground must be 25 ohms.  If it is higher, then you must place a second ground rod.  There is no requirement to retest the resistance.  In practice, for a residential structure, most electricians place two ground rods and call it done.  This does not create the best ground, but it meets the bare minimum of the code.  I do not know of an equivalent requirement in the British Standards.

There are other standards that recommend a specific resistance-to-ground, depending on the type of system you are working with.  Here are two such examples:

ANSI/BICSI 002: Data Center Design and Implementation Best Practices

Recommends 5 Ohms Maximum, but recommends 3 Ohms for Class F2 & F3 Data Centers, and 1 Ohm for Class F4 Data Centers

IEEE 142: Recommended Practice for Grounding of Industrial and Commercial Power Systems (The Green Book)

3.3.4.6 Power stations and substations

“For satisfactory lightning protection, substation grounding network resistance must not exceed 5 ohm; for large stations lower values are more desirable.”

4.1.3 Recommended acceptable values

“Resistances in the 1 ohm to 5 ohm range are generally found suitable for industrial plant substations and buildings and large

commercial installations.”

Generally, we recommend a design goal of a resistance-to-ground less than 5 ohms for most installations.  For substations or sites with sensitive electronics, we recommend a design goal of a resistance-to-ground of less than 1 ohm.

The Engineering Experts at E&S Grounding Solutions

### Related Posts

#### Grounding of metal buildings

PJ Asked:Inspector requires grounding of metal building, I plan to use a rebar in slab to tie to metal frame in another place?

#### What is the mathematical formula for calculating the...

Slamat Asked:What is the mathematical formula for calculating the resistance-to-ground of parallel electrodes?

#### Why are 94Hz, 105Hz, 111Hz, and 128Hz frequencies used for earth...

Numerous studies going back many decades have shown that ground resistance measurements should be conducted using a true Direct-Current (0 Hz) source with an Induced-Polarization (IP) capacity. In...