+1 310.318.7151

Mon - Fri: 9:00AM - 6:00PM

info@esgrounding.com

# How to get a grounding rod below 1ohm ground resistance? How to get a grounding rod below 1ohm ground resistance?

To reduce the resistance to ground, you have two choices:

• A) drive your ground rod deeper or

Based on soil resistivity data, we can calculate scenario A.  However, we can estimate the resistance to ground using scenario B.  Multiple ground rods yield a lower resistance to ground than a single rod.

If your ground rods are placed at least one rod length apart, you can use a formula to estimate the earth resistance of multiple grounding rods.  So, if you are using 10-foot ground rods, you must place them at least 10 feet apart.  Actually, twice the length (20 feet) is ideal if you have the space.

You can divide the resistance of a single ground rod by the total number of rods and then multiplied by a factor F supplied in IEEE Standard 142—Recommended Practice for Grounding of Industrial and Commercial Power Systems (i.e. “The Green Book”).

Table 4-6—Multiplying factors for multiple rods (excerpt)

• F (2 rods) = 1.16
• F (3 rods) = 1.29
• F (4 rods) = 1.36

Thus if your first ground rod measures 2.5 ohms, we would expect the resistance of multiple rods to be the following:

• Resistance (2 rods) = 2.5 ohms / 2 rods * 1.16 = 1.45 ohms
• Resistance (3 rods) = 2.5 ohms / 3 rods * 1.29 = 1.075 ohms
• Resistance (4 rods) = 2.5 ohms / 4 rods * 1.36 = 0.85 ohms

To reach your goal of 1-ohm earth resistance, you will need three or four rods total.  These can be placed in a row or at the corners of a 10-foot by 10-foot square.  A final measurement will let you know if you have reached your 1-ohm goal.

The Engineering Experts at E&S Grounding Solutions

### Related Posts

#### How To Do Electrical Grounding System Testing

The measurement of ground resistance for an earth electrode system is very important. It should be done when the electrode is first installed, and then at periodic intervals thereafter. This ensures...

#### What Is Electrical Grounding?

What Is Electrical Grounding? Electrical grounding or “Grounding” originally began as a safety measure used to help prevent people from accidentally coming in contact with electrical hazards. Think...

#### Grounding Electrode Test Wells

Grounding Electrode Test WellsThe purpose of a ground test well is two-fold: to be able to quickly and easily measure resistance-to-ground of the grounding electrode and/or to measure point-to-point...